The NC704 Maglock engages to lock the door when the NC702 Door Controller detects an SF701 Resident Tag or an SF702 Asset Tag. The maglock remains engaged as long as the door controller detects a tag in its activation field. When the tag leaves the activation field, the maglock disengages after a selectable period of time (0–120 seconds).
When using NC704 Maglocks with a Tek-CARE®700 system, an NC706 Fire Panel Interface is required. This enables the maglock to automatically disengage when the facility’s fire alarm is activated, allowing residents and staff to exit. The maglock will also disengage when power is lost.
The maglock incorporates delayed egress circuitry that complies with NFPA 101 Life Safety Codes 5-22.214.171.124. When a maintained force (less than 15 pounds required) is applied to the door for 15–18 seconds, the lock will release. An audible tone annunciates both countdown and release. When the lock releases, the red LED turns solid green and the alarm sounds continuously.
The NC704 Maglock is specially designed for low current consumption and and easy integration with the NC702 Door Controller. It is powered by the door controller and doesn’t require secondary power.
- Dimensions: 11.0″ × 3.0″ × 2.75″
- Armature Size: 7.375″ × 2.3125″ × 0.5″
- Weight: 11 pounds
- Power Use: 12 V AC/DC, 300mA–450mA
- Cable: non-shielded 18-gauge, 6-conductor
- Environment: 32°–120° F., indoor use only
- Construction: Aluminum with a satin finish
- Mounting: Five 1″ #10 self tapping screws
- Holding Force: 1,200 pounds
One (1) year manufacturer's warranty plus an exclusive one (1) year BuyTekTone.com extended manufacturer's warranty.*